30 CFR 56.12028 - Testing grounding systems.
Continuity and resistance of grounding systems shall be tested immediately after installation, repair, and modification; and annually thereafter. A record of the resistance measured during the most recent tests shall be made available on a request by the Secretary or his duly authorized representative.
Title 30 published on 2013-07-01
no entries appear in the Federal Register after this date.