Flammable or combustible liquid storage buildings or rooms.
(a) Storage buildings or storage rooms in which flammable or combustible liquids, including grease, are stored and that are within 100 feet of any person's work station shall be ventilated with a sufficient volume of air to prevent the accumulation of flammable vapors.
(b) In addition, the buildings or rooms shall be—
(1) Constructed to meet a fire resistance rating of at least one hour; or
(2) Equipped with an automatic fire suppression system; or
(3) Equipped with an early warning fire detection device that will alert any person who could be endangered by a fire, provided that no person's work station is in the building.
(c) Flammable or combustible liquids in use for day-to-day maintenance and operational activities are not considered in storage under this standard.
Title 30 published on 2012-07-01
no entries appear in the Federal Register after this date.
This is a list of United States Code sections, Statutes at Large, Public Laws, and Presidential Documents, which provide rulemaking authority for this CFR Part.