30 CFR 56.6402 - Deenergized circuits near detonators.
Electrical distribution circuits within 50 feet of electric detonators at the blast site shall be deenergized. Such circuits need not be deenergized between 25 to 50 feet of the electric detonators if stray current tests, conducted as frequently as necessary, indicate a maximum stray current of less than 0.05 amperes through a 1-ohm resistor as measured at the blast site.
Title 30 published on 2014-07-01
no entries appear in the Federal Register after this date.