40 CFR Part 76, Appendix B to Part 76 - Procedures and Methods for Estimating Costs of Nitrogen Oxides Controls Applied to Group 1, Boilers
prev | next
Appendix B to Part 76—Procedures and Methods for Estimating Costs of Nitrogen Oxides Controls Applied to Group 1, Boilers
1. Purpose and Applicability
This technical appendix specifies the procedures, methods, and data that the Administrator will use in establishing “***the degree of reduction achievable through this retrofit application of the best system of continuous emission reduction, taking into account available technology, costs, and energy and environmental impacts; and which is comparable to the costs of nitrogen oxides controls set pursuant to subsection (b)(1) (of section 407 of the Act).” In developing the allowable NOX emissions limitations for Group 2 boilers pursuant to subsection (b)(2) of section 407 of the Act, the Administrator will consider only those systems of continuous emission reduction that, when applied on a retrofit basis, are comparable in cost to the cost in constant dollars of low NOX burner technology applied to Group 1, Phase I boilers.
The Administrator will evaluate the capital cost (in dollars per kilowatt electrical ($/kW)), the operating and maintenance costs (in $/year), and the cost-effectiveness (in annualized $/ton NOX removed) of installed low NOX burner technology controls over a range of boiler sizes (as measured by the gross electrical capacity of the associated generator in megawatt electrical (MW)) and utilization rates (in percent gross nameplate capacity on an annual basis) to develop estimates of the capital costs and cost effectiveness for Group 1, Phase I boilers. The following units will be excluded from these determinations of the capital costs and cost effectiveness of NOX controls set pursuant to subsection (b)(1) of section 407 of the Act: (1) Units employing an alternative technology, or overfire air as applied to wall-fired boilers or separated overfire air as applied to tangentially fired boilers, in lieu of low NOX burner technology for reducing NOX emissions; (2) units employing no controls, only controls installed before November 15, 1990, or only modifications to boiler operating parameters (e.g., burners out of service or fuel switching) for reducing NOX emissions; and (3) units that have not achieved the applicable emission limitation.
2. Average Capital Cost for Low NOX Burner Technology Applied to Group 1 Boilers
The Administrator will use the procedures, methods, and data specified in this section to estimate the average capital cost (in $/kW) of installed low NOX burner technology applied to Group 1 boilers.
2.1Using cost data submitted pursuant to the reporting requirements in section 4 below, boiler-specific actual or estimated actual capital costs will be determined for each unit in the population specified in section 1 above for assessing the costs of installed low NOX burner technology. The scope of installed low NOX burner technology costs will include the following capital costs for retrofit application: (1) For the burner portion—burners or air and coal nozzles, burner throat and waterwall modifications, and windbox modifications; and, where applicable, (2) for the combustion air staging portion—waterwall modifications or panels, windbox modifications, and ductwork, and (3) scope adders or supplemental equipment such as replacement or additional fans, dampers, or ignitors necessary for the proper operation of the low NOX burner technology. Capital costs associated with boiler restoration or refurbishment such as replacement of air heaters, asbestos abatement, and recasing will not be included in the cost basis for installed low NOX burner technology. The scope of installed low NOX burner technology retrofit capital costs will include materials, construction and installation labor, engineering, and overhead costs.
2.2Using gross nameplate capacity (in MW) for each unit as reported in the National Allowance Data Base (NADB), boiler-specific capital costs will be converted to a $/kW basis.
2.3Capital cost curves ($/kW versus boiler size in MW) or equations for installed low NOX burner technology retrofit costs will be developed for: (1) Dry bottom wall fired boilers (excluding units applying cell burner technology) and (2) tangentially fired boilers.
4. Reporting Requirements
4.1The following information is to be submitted by each designated representative of a Phase I affected unit subject to the reporting requirements of § 76.14(c):
4.1.1Schedule and dates for baseline testing, installation, and performance testing of low NOX burner technology.
4.1.2Estimates of the annual average baseline NOX emission rate, as specified in section 3.1.1, and the annual average controlled NOX emission rate, as specified in section 3.1.2, including the supporting continuous emission monitoring or other test data.
4.1.3Copies of pre-retrofit and post-retrofit performance test reports.
4.1.4Detailed estimates of the capital costs based on actual contract bids for each component of the installed low NOX burner technology including the items listed in section 2.1. Indicate number of bids solicited. Provide a copy of the actual agreement for the installed technology.
4.1.5Detailed estimates of the capital costs of system replacements or upgrades such as coal pipe changes, fan replacements/upgrades, or mill replacements/upgrades undertaken as part of the low NOX burner technology retrofit project.
4.1.6Detailed breakdown of the actual costs of the completed low NOX burner technology retrofit project where low NOX burner technology costs (section 4.1.4) are disaggregated, if feasible, from system replacement or upgrade costs (section 4.1.5).
4.1.7Description of the probable causes for significant differences between actual and estimated low NOX burner technology retrofit project costs.
4.1.8Detailed breakdown of the burner and, if applicable, combustion air staging system annual operating and maintenance costs for the items listed in section 3.3 before and after the installation, shakedown, and/or optimization of the installed low NOX burner technology. Include estimates and a description of the probable causes of the incremental annual operating and maintenance costs (or savings) attributable to the installed low NOX burner technology.
4.2All capital cost estimates are to be broken down into materials costs, construction and installation labor costs, and engineering and overhead costs. All operating and maintenance costs are to be broken down into maintenance materials costs, maintenance labor costs, operating labor costs, and fan electricity costs. All capital and operating costs are to be reported in dollars with the year of expenditure or estimate specified for each component.
Title 40 published on 2014-07-01
no entries appear in the Federal Register after this date.