46 CFR 131.899 - Fire dampers.
prev | next
Each fire damper installed within the boundary of a space protected by a fixed fire extinguishing system must be fitted with an indicator showing whether the damper is open or closed and must be marked with red letters at least 13 millimeters (1/2-inch) high stating “FIRE DAMPER” and, as otherwise appropriate, identifying the space served by the fire damper.
Title 46 published on 2013-10-01
no entries appear in the Federal Register after this date.