Trolley wires and trolley feeder wires shall be provided with cutout switches at intervals of not more than 2,000 feet and near the beginning of all branch lines.
(b) Overcurrent protection devices
Trolley wires and trolley feeder wires shall be provided with overcurrent protection.
(c) Location of wires
Trolley wires and trolley feeder wires, high-voltage cables and transformers shall not be located inby the last open crosscut and shall be kept at least 150 feet from pillar workings.
(d) Adequate insulation and guard devices; promulgation of safety guidelines
Trolley wires, trolley feeder wires, and bare signal wires shall be insulated adequately where they pass through doors and stoppings, and where they cross other power wires and cables. Trolley wires and trolley feeder wires shall be guarded adequately
(1) at all points where men are required to work or pass regularly under the wires;
(2) on both sides of all doors and stoppings; and
(3) at man-trip stations. The Secretary or his authorized representatives shall specify other conditions where trolley wires and trolley feeder wires shall be adequately protected to prevent contact by any person, or shall require the use of improved methods to prevent such contact. Temporary guards shall be provided where trackmen and other persons work in proximity to trolley wires and trolley feeder wires.
The table below lists the classification updates, since Jan. 3, 2012, for this section. Updates to a broader range of sections may be found at the update page for containing chapter, title, etc.
The most recent Classification Table update that we have noticed was Tuesday, August 13, 2013
An empty table indicates that we see no relevant changes listed in the classification tables. If you suspect that our system may be missing something, please double-check with the Office of the Law Revision Counsel.
Description of Change
Statutes at Large
LII has no control over and does not endorse any external Internet site that contains links to or references LII.