21 CFR 1250.89 - Swimming pools.
(a) Fill and draw swimming pools shall not be installed or used.
(b) Swimming pools of the recirculation type shall be equipped so as to provide complete circulation, replacement, and filtration of the water in the pool every six hours or less. Suitable means of chlorination and, if necessary, other treatment of the water shall be provided to maintain the residual chlorine in the pool water at not less than 0.4 part per million and the pH (a measure of the hydrogen ion concentration) not less than 7.0.
(c) Flowing-through types of salt water pools shall be so operated that complete circulation and replacement of the water in the pool will be effected every 6 hours or less. The water delivery pipe to the pool shall be independent of all other pipes and shall originate at a point where maximum flushing of the pump and pipe line is effected after leaving polluted waters.
Title 21 published on 09-Nov-2018 03:23
The following are ALL rules, proposed rules, and notices (chronologically) published in the Federal Register relating to 21 CFR Part 1250 after this date.