29 CFR 1926.1408 - Power line safety (up to 350 kV) - equipment operations.
(1)Identify the work zone by either:
(i) Demarcating boundaries (such as with flags, or a device such as a range limit device or range control warning device) and prohibiting the operator from operating the equipment past those boundaries, or
(2) Determine if any part of the equipment, load line or load (including rigging and lifting accessories), if operated up to the equipment's maximum working radius in the work zone, could get closer than 20 feet to a power line. If so, the employer must meet the requirements in Option (1), Option (2), or Option (3) of this section, as follows:
(ii)Option (2) - 20 foot clearance. Ensure that no part of the equipment, load line, or load (including rigging and lifting accessories), gets closer than 20 feet to the power line by implementing the measures specified in paragraph (b) of this section.
(iii)Option (3) - Table A clearance.
(B) Determine if any part of the equipment, load line or load (including rigging and lifting accessories), while operating up to the equipment's maximum working radius in the work zone, could get closer than the minimum approach distance of the power line permitted under Table A (see § 1926.1408). If so, then the employer must follow the requirements in paragraph (b) of this section to ensure that no part of the equipment, load line, or load (including rigging and lifting accessories), gets closer to the line than the minimum approach distance.
(1) Conduct a planning meeting with the operator and the other workers who will be in the area of the equipment or load to review the location of the power line(s), and the steps that will be implemented to prevent encroachment/electrocution.
(2) If tag lines are used, they must be non-conductive.
(3) Erect and maintain an elevated warning line, barricade, or line of signs, in view of the operator, equipped with flags or similar high-visibility markings, at 20 feet from the power line (if using Option (2) of this section) or at the minimum approach distance under Table A (see § 1926.1408) (if using Option (3) of this section). If the operator is unable to see the elevated warning line, a dedicated spotter must be used as described in § 1926.1408(b)(4)(ii) in addition to implementing one of the measures described in §§ 1926.1408(b)(4)(i), (iii), (iv) and (v).
(4) Implement at least one of the following measures:
(ii) A dedicated spotter who is in continuous contact with the operator. Where this measure is selected, the dedicated spotter must:
(A) Be equipped with a visual aid to assist in identifying the minimum clearance distance. Examples of a visual aid include, but are not limited to: A clearly visible line painted on the ground; a clearly visible line of stanchions; a set of clearly visible line-of-sight landmarks (such as a fence post behind the dedicated spotter and a building corner ahead of the dedicated spotter).
(B) Be positioned to effectively gauge the clearance distance.
(D) Give timely information to the operator so that the required clearance distance can be maintained.
(iii) A device that automatically warns the operator when to stop movement, such as a range control warning device. Such a device must be set to give the operator sufficient warning to prevent encroachment.
(c)Voltage information. Where Option (3) of this section is used, the utility owner/operator of the power lines must provide the requested voltage information within two working days of the employer's request.
(d)Operations below power lines.
(1) No part of the equipment, load line, or load (including rigging and lifting accessories) is allowed below a power line unless the employer has confirmed that the utility owner/operator has deenergized and (at the worksite) visibly grounded the power line, except where one of the exceptions in paragraph (d)(2) of this section applies.
(ii) For equipment with non-extensible booms: The uppermost part of the equipment, with the boom at true vertical, would be more than 20 feet below the plane of the power line or more than the Table A of this section minimum clearance distance below the plane of the power line.
(iii) For equipment with articulating or extensible booms: The uppermost part of the equipment, with the boom in the fully extended position, at true vertical, would be more than 20 feet below the plane of the power line or more than the Table A of this section minimum clearance distance below the plane of the power line.
(e)Power lines presumed energized. The employer must assume that all power lines are energized unless the utility owner/operator confirms that the power line has been and continues to be deenergized and visibly grounded at the worksite.
(f) When working near transmitter/communication towers where the equipment is close enough for an electrical charge to be induced in the equipment or materials being handled, the transmitter must be deenergized or the following precautions must be taken:
(2) If tag lines are used, they must be non-conductive.
(C) The safest means of evacuating from equipment that may be energized.
(D) The danger of the potentially energized zone around the equipment (step potential).
(F) Safe clearance distance from power lines.
(iii) Power lines are presumed to be uninsulated unless the utility owner/operator or a registered engineer who is a qualified person with respect to electrical power transmission and distribution confirms that a line is insulated.
(h) Devices originally designed by the manufacturer for use as: A safety device (see § 1926.1415), operational aid, or a means to prevent power line contact or electrocution, when used to comply with this section, must meet the manufacturer's procedures for use and conditions of use.
Table A - Minimum Clearance Distances
(nominal, kV, alternating current)
|Minimum clearance distance
|up to 50||10|
|over 50 to 200||15|
|over 200 to 350||20|
|over 350 to 500||25|
|over 500 to 750||35|
|over 750 to 1,000||45|
|over 1,000||(as established by the utility owner/operator or registered professional engineer who is a qualified person with respect to electrical power transmission and distribution).|
Note: The value that follows “to” is up to and includes that value. For example, over 50 to 200 means up to and including 200kV.
- 29 CFR 1926.1408 — Power Line Safety (Up to 350 kV) - Equipment Operations.
- 29 CFR 1926.1411 — Power Line Safety - While Traveling Under or Near Power Lines With No Load.
- 29 CFR 1926.1427 — Operator Qualification and Certification.
- 29 CFR 1926.1426 — Free Fall and Controlled Load Lowering.
- 29 CFR 1926.1407 — Power Line Safety (Up to 350 kV) - Assembly and Disassembly.
- 29 CFR 1926.1430 — Training.
- 29 CFR 1926.1410 — Power Line Safety (All Voltages) - Equipment Operations Closer Than the Table a Zone.