Conn. Agencies Regs. § 19-411-C12 - Electrical wiring in the machinery space and hoistways
Current through March 4, 2022
Exception: Flexible conduit or armored cables may be used between hoistway risers and limit switches, hoistway door interlocks or contacts and signal or stop buttons and similar devices. All conduits, armored cable, electrical metallic tubing, metal wireways and flexible conduits carrying electrical conductors located within hoistways shall be securely fastened to the hoistway construction or to the guide rails or to the guide rail supports.
The flexible traveling cable, connecting the platform to the stationary hoistway wiring, shall be provided in a flame retardant and moisture resistant outer cover.
The following state regulations pages link to this page.
State regulations are updated quarterly; we currently have two versions available. Below is a comparison between our most recent version and the prior quarterly release. More comparison features will be added as we have more versions to compare.