Kan. Admin. Regs. § 22-7-12 - Aboveground abandonment of underground tanks
Current through Register Vol. 40, No. 39, September 30, 2021
The following state regulations pages link to this page.
State regulations are updated quarterly; we currently have two versions available. Below is a comparison between our most recent version and the prior quarterly release. More comparison features will be added as we have more versions to compare.
(b) The tank owner shall be responsible for:
(1) Purging the tank of vapors;
(2) insuring that explosive concentrations of vapors cannot gather inside the tank; and
(3) insuring that no opening of the tank is accessible to children.
(c) Tanks abandoned for more than twelve months shall then be rendered unusable by the tank owner by disassembly or other appropriate means which shall permit the free circulation of air throughout the tank.
(d) No underground tank shall be reinstalled for aboveground use without being certified for such use by meeting the requirements of UL standard 142 or equivalent. (Authorized by and implementing K.S.A. 1991 Supp. 31-133; effective May 10, 1993.)
This article was formerly entitled, "Bulk Oil and Service Stations; Flammable Liquids." Regulations formerly appearing hereunder were revoked.