Kan. Admin. Regs. § 22-7-7 - Approval of plans
Current through Register Vol. 40, No. 39, September 30, 2021
The following state regulations pages link to this page.
State regulations are updated quarterly; we currently have two versions available. Below is a comparison between our most recent version and the prior quarterly release. More comparison features will be added as we have more versions to compare.
(b) The plans approval requirements applies to the following:
(1) Each new installation of tanks containing flammable or combustible liquids in the following amounts:
(A) Any state, county or local governmental unit installing tanks of 660 gallons or more capacity;
(B) any Industrial or Business company installing tanks of 660 gallons or more capacity;
(C) any agricultural farm installation of tanks of 1,100 gallons or more capacity; and
(D) any tank installed for the retail sale of flammable or combustible product through dispenser devices;
(2) any modifications to or replacements of tanks or piping at any establishment or facility meeting the requirements of (1); and
(3) any installation of new dispenser locations at any establishments or facility meeting the requirements of (1). This does not include the routine replacement of dispensers at existing sites.
(c) This plans approval requirements is in addition to any local jurisdiction requirements necessary to meet local zoning or permit approval and additional local requirements. In the event of a dispute as to whether or not the drawings or blueprints show conformity with the applicable requirements of these regulations, the local decision can be appealed to the state fire marshal in accordance with statutory provisions.
(d) All submitted drawings shall include the following minimum information:
(1) The name of the person, firm, or corporation proposing the installation, the location thereof and the adjacent streets or highways;
(2) for bulk plants, in addition to any applicable features required under (4) and (5) of this section, the plot of ground to be utilized and its immediate surroundings, including any structures of value located on adjacent properties within 100 feet of the property line, on all sides, the complete layout of buildings, tanks, loading and unloading docks, and the types of construction of each building;
(3) for service stations, in addition to any applicable features required under (4) and (5) of this section, the plot of ground to be utilized and the complete layout of buildings, drives, and dispensing equipment;
(4) for above ground storage, the location and capacity of each tank, the dimensions of each tank, the class and name of liquid to be stored in each tank, the type of any tank supports, the types and sizes of normal and emergency valves, and the location of pumps and other facilities by which the tanks are filled or drained;
(5) in the case of underground storage, the location and capacity of each tank, the class and name of liquid to be stored in each tank, and the location of fill, gauge and vent pipes and openings; and
(6) in the case of installation for storage, handling or use of flammable liquids within the buildings or enclosures at any establishment or occupancy covered in this section, such detail as to show whether applicable requirements are met. (Authorized by and implementing K.S.A. 1991 Supp. 31-133; effective May 10, 1993.)
This article was formerly entitled, "Bulk Oil and Service Stations; Flammable Liquids." Regulations formerly appearing hereunder were revoked.