02-658 C.M.R. ch. 110, § 9 - SOLID FUEL IN GARAGES
Current through 2022-14, April 6, 2022
Except as described below, solid fuel burning appliances cannot be installed in any garage unless installed in a separate room either in or attached to the garage and that is accessible only from the outside. For a Major Repair Garage, the fire wall separation shall be two (2) hours. For Minor Repair and Parking Garages, the fire wall separation shall be one (1) hour. All combustion air must be taken from outside the building.
Note: Refer to NFPA #30A for further information.
Exception: Solid fuel burning appliances using sealed combustion systems for which the air for combustion is taken from the outside may be installed in garages of one and two-family dwellings.
The following state regulations pages link to this page.
State regulations are updated quarterly; we currently have two versions available. Below is a comparison between our most recent version and the prior quarterly release. More comparison features will be added as we have more versions to compare.