N.J. Admin. Code § 7:9A-4.3 - Distances
Current through Register Vol. 54, No. 7, April 4, 2022
The minimum separation distance between the various components of the system and the other features listed shall conform to and be maintained in accordance with Table 4.3 below. The location of a new well must be in conformance with the requirements of N.J.A.C. 7:9D. No permit or waiver issued outside of this chapter by any local, State or Federal entity shall be construed to permit deviation from or a waiver of the separation distances requirements listed in the Table 4.3 below.
Table 4.3 Minimum Required Separation Distances (feet)
|Component||Well or Suction Line||Water Service Line||Water Course(1,12)||Occupied Building||Property Line (15)||Disposal Field||Existing Seepage Pit or Cesspool||In-ground Swimming Pool|
<(1)> This distance may be increased as determined by a local, State or Federal entity having authority for establishing separation distances, including, but not limited to, wetlands protection, stream encroachment and riparian corridor.
<(2)> Where excessively coarse soils or fractured rock substrata are encountered, these distances may be increased by the administrative authority.
<(3)> This distance may be decreased only in the case of an interceptor drain allowed in N.J.A.C 7:9A-10.7(d).
<(4)> This distance may be decreased by the administrative authority, to a minimum of 50 feet when either the well is provided with a water-tight casing to a depth of 100 feet or more, or where the casing is sealed into an impervious stratum which separates the waterbearing stratum from the layer of soil used for sanitary sewage disposal. N.J.A.C. 7:9D shall govern whenever the well under consideration has been installed after July 13, 1979.
<(5)> These distances may be reduced by one-half if the water course is a footing drain with an invert elevation higher than the bottom of the disposal field or more than four feet above the level of the seasonally high water table.
<(6)> May be reduced to five feet with special approval of the administrative authority.
<(7)> May be reduced to 15 feet from disposal field and 30 feet from seepage pit for portions of the building constructed either on a slab foundation or over a continuous dust cap which is at or above natural or finished grade, whichever is higher only.
<(8)> This distance applies to disposal fields serving separate realty improvements but not to disposal fields which are part of a split system serving a single realty improvement.
<(9)> Applies only to seepage pits allowed as prescribed in 7:9A-7.6.
<(10)> In no case shall the distance be less than three times the pit diameter.
<(11)> These distances shall be measured from the outermost margin of the disposal bed or trench in the case of conventional and soil replacement bottom-lined installations, from the outermost lateral extension of suitable fill in the case of soil replacement fill-enclosed and mounded soil replacement installations, or the edge of the required lateral suitable fill extension in the case of mounded installations.
<(12)> For the purposes of this section, the setback distance for a water course shall apply to a stormwater management basin. The setback distance from a stormwater management basin shall be measured from the elevation contour that is coincident with the high water mark.
<(13)> The setback distance from a seepage pit shall be 150 feet from a well and 100 feet from a suction line.
<(14)> For the purposes of measuring separation distance requirements, a D-Box shall include all piping and appurtenances associated with the effluent distribution network from the outlet of the septic tank to the disposal area.
<(15)> This separation distance requirement may be reduced to zero feet in cases where either of the following is provided to the administrative authority prior to obtaining a construction approval for the infringing system or its component:
The following state regulations pages link to this page.
State regulations are updated quarterly; we currently have two versions available. Below is a comparison between our most recent version and the prior quarterly release. More comparison features will be added as we have more versions to compare.