29 CFR 1910.159 - Automatic sprinkler systems.
(a)Scope and application.
(2) For automatic sprinkler systems used to meet OSHA requirements and installed prior to the effective date of this standard, compliance with the National Fire Protection Association (NFPA) or the National Board of Fire Underwriters (NBFU) standard in effect at the time of the system's installation will be acceptable as compliance with this section.
(c)General requirements -
(i) All automatic sprinkler designs used to comply with this standard shall provide the necessary discharge patterns, densities, and water flow characteristics for complete coverage in a particular workplace or zoned subdivision of the workplace.
(2)Maintenance. The employer shall properly maintain an automatic sprinkler system installed to comply with this section. The employer shall assure that a main drain flow test is performed on each system annually. The inspector's test valve shall be opened at least every two years to assure that the sprinkler system operates properly.
(3)Acceptance tests. The employer shall conduct proper acceptance tests on sprinkler systems installed for employee protection after January 1, 1981, and record the dates of such tests. Proper acceptance tests include the following:
(i) Flushing of underground connections;
(ii) Hydrostatic tests of piping in system;
(iii) Air tests in dry-pipe systems;
(iv) Dry-pipe valve operation; and
(v) Test of drainage facilities.
(4)Water supplies. The employer shall assure that every automatic sprinkler system is provided with at least one automatic water supply capable of providing design water flow for at least 30 minutes. An auxiliary water supply or equivalent protection shall be provided when the automatic water supply is out of service, except for systems of 20 or fewer sprinklers.
(5)Hose connections for fire fighting use. The employer may attach hose connections for fire fighting use to wet pipe sprinkler systems provided that the water supply satisfies the combined design demand for sprinklers and standpipes.
(7)Drainage. The employer shall assure that all dry sprinkler pipes and fittings are installed so that the system may be totally drained.
(iii) The employer shall assure that sprinklers are protected from mechanical damage.
(9)Sprinkler alarms. On all sprinkler systems having more than twenty (20) sprinklers, the employer shall assure that a local waterflow alarm is provided which sounds an audible signal on the premises upon water flow through the system equal to the flow from a single sprinkler.
(10)Sprinkler spacing. The employer shall assure that sprinklers are spaced to provide a maximum protection area per sprinkler, a minimum of interference to the discharge pattern by building or structural members or building contents and suitable sensitivity to possible fire hazards. The minimum vertical clearance between sprinklers and material below shall be 18 inches (45.7 cm).
(11)Hydraulically designed systems. The employer shall assure that hydraulically designed automatic sprinkler systems or portions thereof are identified and that the location, number of sprinklers in the hydraulically de signed section, and the basis of the design is indicated. Central records may be used in lieu of signs at sprinkler valves provided the records are available for inspection and copying by the Assistant Secretary.
- 29 CFR 1910.106 — Flammable Liquids.
- 29 CFR 1910.34 — Coverage and Definitions.
- 29 CFR 1910.107 — Spray Finishing Using Flammable and Combustible Materials.
- 29 CFR 1910.109 — Explosives and Blasting Agents.
- 29 CFR 1910.157 — Portable Fire Extinguishers.
- 29 CFR 1910.160 — Fixed Extinguishing Systems, General.
- 29 CFR 1910.163 — Fixed Extinguishing Systems, Water Spray and Foam.