30 CFR 56.13030 - Boilers.
prev | next
(a) Fired pressure vessels (boilers) shall be equipped with water level gauges, pressure gauges, automatic pressure-relief valves, blowdown piping, and other safety devices approved by the American Society of Mechanical Engineers to protect against hazards from overpressure, flameouts, fuel interruptions and low water level, all as required by the appropriate sections, chapters and appendices listed in paragraphs (b) (1) and (2) of this section.
(b) These gauges, devices and piping shall be designed, installed, operated, maintained, repaired, altered, inspected, and tested by inspectors holding a valid National Board Commission and in accordance with the following listed sections, chapters and appendices:
(1) The ASME Boiler and Pressure Vessel Code, 1977, Published by the American Society of Mechanical Engineers.
Section and Title
IIMaterial Specifications—Part A—Ferrous.
IIMaterial Specifications—Part B—Non-ferrous.
IIMaterial Specifications—Part C—Welding Rods, Electrodes, and Filler Metals.
VIRecommended Rules for Care and Operation of Heating Boilers
VIIRecommended Rules for Care of Power Boilers
(2) The National Board Inspection Code, a Manual for Boiler and Pressure Vessel Inspectors, 1979, published by the National Board of Boiler and Pressure Vessel Inspectors.
Chapter and Title
IGlossary of Terms
IIInspection of Boilers and Pressure Vessels
IIIRepairs and Alterations to Boiler and Pressure Vessels by Welding
IVShop Inspection of Boilers and Pressure Vessels
VInservice Inspection of Pressure Vessels by Authorized Owner-User Inspection Agencies
Appendix and Title
ASafety and Safety Relief Valves
BNon-ASME Code Boilers and Pressure Vessels
CStorage of Mild Steel Covered Arc Welding Electrodes
D-RNational Board “R” (Repair) Symbol Stamp
D-VRNational Board “VR” (Repair of Safety and Safety Relief Valve) Symbol Stamp
D-VR1Certificate of Authorization for Repair Symbol Stamp for Safety and Safety Relief Valves
D-VR2Outline of Basic Elements of Written Quality Control System for Repairers of ASME Safety and Safety Relief Valves
D-VR3Nameplate Stamping for “VR”
EOwner-user Inspection Agencies
(c) Records of inspections and repairs shall be kept in accordance with the requirements of the ASME Boiler and Pressure Vessel Code and the National Board Inspection Code. The records shall be made available to the Secretary or his authorized representative.
(d) Sections of the ASME Boiler and Pressure Vessel Code, 1977, listed in paragraph (b)(1) of this section, and chapters and appendices of the National Board Inspection Code, 1979, listed in paragraph (b)(2) of this section, are incorporated by reference and made a part of this standard. These publications may be obtained from the publishers, the American Society of Mechanical Engineers, 22 Law Drive, P.O. Box 2900, Fairfield, New Jersey 07007, Phone: 800-843-2763 (toll free); http://www.asme.org , and the National Board of Boiler and Pressure Vessel Inspectors, 1055 Crupper Avenue, Columbus, Ohio 43229. The publications may be examined at any Metal and Nonmetal Mine Safety and Health District Office of the Mine Safety and Health Administration.
[50 FR 4054, Jan. 29, 1985, as amended at 71 FR 16667, Apr. 3, 2006]
Title 30 published on 2014-07-01.
No entries appear in the Federal Register after this date, for 30 CFR Part 56.