46 CFR § 105.13 - Electrical fittings and fixtures.
(a) In compartments or areas containing tanks or pumps handling petroleum products other than Grade E products, no electrical fittings, fixtures, or equipment may be installed or used unless approved for a Class I, Group D hazardous location and labeled as such by UL or another recognized laboratory.
(b) All electrical equipment, fixtures, and fittings located within 10 feet of a vent outlet or a dispensing outlet must be explosion-proof and labeled as such by UL or another recognized laboratory, as suitable for Class I, Group D atmospheres.
(c) All electrical equipment must be grounded to the vessel's common ground.
(d) Tanks, containers, and associated piping systems in use prior to December 1, 1969, on a vessel the construction of which was contracted for before May 31, 1976, are exempt from the requirements of this section provided they are maintained in a condition that the Officer in Charge, Marine Inspection, finds satisfactory, and provided that major repairs or replacement of exempted equipment and systems is in accordance with this part.
The following state regulations pages link to this page.