46 CFR § 111.12-9 - Generator cables.
(a) The current-carrying capacity of generator cables must not be:
(1) Less than 115 percent of the continuous generator rating; or
(2) Less than 115 percent of the overload for a machine with a 2 hour or greater overload rating.
(b) Generator cables must not be in the bilges.
The following state regulations pages link to this page.