46 CFR 169.678 - Main distribution panels and switchboards.
(a) A distribution panel to which the generator leads are connected, and from which the electric leads throughout the vessel directly or indirectly receive their electric power is a switchboard.
(b) Each switchboard must have a driphood or an equivalent means of protecting against falling liquid.
(c) Nonconductive deck materials, mats, or gratings must be provided in front of each switchboard.
(d) If the switchboard is accessible from the rear, nonconductive deck material, mats, or gratings must be provided in the rear of the switchboard.
(e) Metal cases of instruments and secondary windings of instrument transformers must be grounded.
(f) Each switchboard must be placed in a location that is accessible, adequately ventilated, and as dry as practicable. All uninsulated current carrying parts must be mounted on nonabsorbent, noncombustible, high dielectric insulating material.
(g) Each switchboard must be of the dead front type.
(h) Each switchboard must have front and, if accessible from the back, rear non-conducting hand rails except on vessels where the surrounding bulkheads and decks are of an insulating material such as fiberglass or wood.
Title 46 published on 09-May-2017 04:27
The following are ALL rules, proposed rules, and notices (chronologically) published in the Federal Register relating to 46 CFR Part 169 after this date.