46 CFR 169.682 - Distribution and circuit loads.
(a) Except as provided in paragraph (b) of this section, the connected load on a lighting branch circuit must not exceed 80 percent of the rating of the overcurrent protective device, computed using the greater of -
(1) The lamp sizes to be installed; or
(2) 50 watts per outlet.
(b) Circuits supplying electrical discharge lamps must be computed using the ballast input current.
(c) The branch circuit cables for motor and lighting loads must be no smaller than No. 14 AWG.
Title 46 published on 09-May-2017 04:27
The following are ALL rules, proposed rules, and notices (chronologically) published in the Federal Register relating to 46 CFR Part 169 after this date.