49 CFR 173.301a - Additional general requirements for shipment of specification cylinders.
(a) General. The requirements in this section are in addition to the requirements in § 173.301 and apply to the shipment of gases in specification cylinders.
(b) Authorized cylinders not marked with a service pressure. For authorized cylinders not marked with a service pressure, the service pressure is designated as follows:
|Specification marking||Service Pressure psig|
(c) Cylinder pressure at 21 °C (70 °F). The pressure in a cylinder at 21 °C (70 °F) may not exceed the service pressure for which the cylinder is marked or designated, except as provided in § 173.302a(b). For certain liquefied gases, the pressure at 21 °C (70 °F) must be lower than the marked service pressure to avoid having a pressure at a temperature of 55 °C (131 °F) that is greater than permitted.
(1) For a cylinder filled with acetylene, liquefied nitrous oxide, or carbon dioxide.
(3) The pressure at 55 °C (131 °F) of Hazard Zone A and Hazard Zone B materials may not exceed the service pressure of the cylinder. Sufficient outage must be provided so that the cylinder will not be liquid full at 55 °C (131 °F).
(e) Grandfather clause. A cylinder in domestic use prior to the date on which the specification for the cylinder was first made effective may be used if the cylinder has been properly tested and otherwise conforms to the requirements applicable to the gas with which it is charged.
Title 49 published on 2015-10-01
The following are ALL rules, proposed rules, and notices (chronologically) published in the Federal Register relating to 49 CFR Part 173 after this date.