(a) The well shall be so constructed that a pump of capacity equal to the desired yield can be installed and operated for different yields.
(b) Any water used shall be disinfected or of drinking water quality.
(c) Any chemicals or other additives used in drilling shall be cleaned out from the well.
(d) Rock cuttings shall be cleaned out of the well.
The well shall be tested as provided by Section 19-13-B51
of the Public Health Code.
(f) The well driller shall prepare and maintain a log on forms supplied by the Board, and shall submit copies of the log to the Board and to the owner or owners of the well, respectively. The log shall clearly identify the location of the well upon the premises.
(g) Well development shall be performed only by properly registered persons.
(h) Subcontracted work shall be performed only by properly registered persons.
(i) No solder containing more than 0.2 per cent lead shall be used in making joints and fittings in any public or private potable water supply system or any water user's pipelines.