Ill. Admin. Code tit. 8, § 215.60 - Filling Densities
a) Filling density is limited to 85% capacity by volume at 60°F.
b) The filling densities for non-refrigerated containers shall not exceed the following:
1) Uninsulated aboveground 56%;
2) Insulated aboveground 57%.
c) US Department of Transportation containers shall be filled in accordance with 49 CFR 173.315(m)(5).
d) If containers are to be filled according to liquid level by any gauging method other than a fixed length dip tube gauge, each container shall have a thermometer well and thermometer so that the internal liquid temperature can be easily determined and the amount of liquid and vapor in the container corrected to a 60°F basis.
Amended at 27 Ill. Reg. 9922, effective July 1, 2003
State regulations are updated quarterly; we currently have two versions available. Below is a comparison between our most recent version and the prior quarterly release. More comparison features will be added as we have more versions to compare.
No prior version found.