02-658 C.M.R. ch. 13, § 4 - Installations
Current through 2022-14, April 6, 2022
Whenever a furnace, direct-fired hot water heater, or boiler is installed, the total installation must be brought into compliance with the requirements of NFPA #54 (2012 edition), NFPA#58 (2011 edition) and all other rules of the BoardBEFORE the furnace, direct-fired water heater, or boiler is fired. Prior to leaving the installation (whether installed inside or outside any structure) unsupervised, the licensed propane and natural gas technician must observe, inspect, and test the equipment to ensure that the installation is operating safely and properly and meets all applicable rules of the Board.
When an appliance other than a furnace, direct-fired water heater, or boiler is installed, the following must be done:
When installing a vented central heating appliance, the installer must conduct a combustion efficiency test, unless prohibited by the manufacturer, and must post a copy of the test results on-site.
The following state regulations pages link to this page.
State regulations are updated quarterly; we currently have two versions available. Below is a comparison between our most recent version and the prior quarterly release. More comparison features will be added as we have more versions to compare.