Minn. R. 1305.0915 - IBC [F] SECTION 915, CARBON MONOXIDE DETECTION
IBC [F] section 915.1 and subsection 915.1.1 are amended to read as follows:
Exception: In multi-family dwellings, approved and operational carbon monoxide alarms may be installed between 15 and 25 feet of carbon monoxide-producing central fixtures and equipment provided there is a centralized alarm system or other approved mechanism for responsible parties to hear the alarms at all times.
(Sections 915.1.2 through 915.1.6 remain unchanged.)
IBC [F] section 915.2 and subsections 915.2.1 and 915.2.2 are amended to read as follows:
Exception: Carbon monoxide detection shall be allowed to be installed outside of each separate sleeping area within ten feet of the sleeping unit where the sleeping unit or its attached bathroom does not contain a fuel-burning appliance and is not served by a forced air furnace.
(Section 915.2.3 remains unchanged.)
State regulations are updated quarterly; we currently have two versions available. Below is a comparison between our most recent version and the prior quarterly release. More comparison features will be added as we have more versions to compare.