S.D. Admin. R. 61:15:07:04 - Automatic sprinkler system requirements
An automatic sprinkler system must be installed in basements of school occupancies when the total area of unseparated uses exceeds 1,500 square feet in floor area. All valves controlling the water supply for automatic sprinkler systems must be electrically supervised when the number of sprinkler heads exceeds 100. All automatic sprinkler systems must have a water-flow switch which activates the building's fire alarm. For uses to be considered as separated, the separation may not be less than as required for a one-hour occupancy separation.
General Authority: SDCL 13-25-2.
Law Implemented: SDCL 13-25-3, 13-25-4.
State regulations are updated quarterly; we currently have two versions available. Below is a comparison between our most recent version and the prior quarterly release. More comparison features will be added as we have more versions to compare.