40 CFR 63.11094 - What are my recordkeeping requirements?
(a) Each owner or operator of a bulk gasoline terminal or pipeline breakout station whose storage vessels are subject to the provisions of this subpart shall keep records as specified in § 60.115b of this chapter if you are complying with options 2(a), 2(b), or 2(c) in Table 1 to this subpart, except records shall be kept for at least 5 years. If you are complying with the requirements of option 2(d) in Table 1 to this subpart, you shall keep records as specified in § 63.1065.
(b) Each owner or operator of a bulk gasoline terminal subject to the provisions of this subpart shall keep records of the test results for each gasoline cargo tank loading at the facility as specified in paragraphs (b)(1) through (3) of this section.
(i)Name of test: Annual Certification Test - Method 27 or Periodic Railcar Bubble Leak Test Procedure.
(iii) Cargo tank identification number.
(iv) Test location and date.
(v) Tester name and signature.
(vi)Witnessing inspector, if any: Name, signature, and affiliation.
(vii)Vapor tightness repair: Nature of repair work and when performed in relation to vapor tightness testing.
(viii)Test results: Test pressure; pressure or vacuum change, mm of water; time period of test; number of leaks found with instrument; and leak definition.
(3) If you are complying with the alternative requirements in § 63.11088(b), you must keep records documenting that you have verified the vapor tightness testing according to the requirements of the Administrator.
(c) As an alternative to keeping records at the terminal of each gasoline cargo tank test result as required in paragraph (b) of this section, an owner or operator may comply with the requirements in either paragraph (c)(1) or paragraph (c)(2) of this section.
(1) An electronic copy of each record is instantly available at the terminal.
(i) The copy of each record in paragraph (c)(1) of this section is an exact duplicate image of the original paper record with certifying signatures.
(2) For facilities that use a terminal automation system to prevent gasoline cargo tanks that do not have valid cargo tank vapor tightness documentation from loading (e.g., via a card lock-out system), a copy of the documentation is made available (e.g., via facsimile) for inspection by the Administrator's delegated representatives during the course of a site visit, or within a mutually agreeable time frame.
(i) The copy of each record in paragraph (c)(2) of this section is an exact duplicate image of the original paper record with certifying signatures.
(d) Each owner or operator subject to the equipment leak provisions of § 63.11089 shall prepare and maintain a record describing the types, identification numbers, and locations of all equipment in gasoline service. For facilities electing to implement an instrument program under § 63.11089, the record shall contain a full description of the program.
(e) Each owner or operator of an affected source subject to equipment leak inspections under § 63.11089 shall record in the log book for each leak that is detected the information specified in paragraphs (e)(1) through (7) of this section.
(1) The equipment type and identification number.
(2) The nature of the leak (i.e., vapor or liquid) and the method of detection (i.e., sight, sound, or smell).
(3) The date the leak was detected and the date of each attempt to repair the leak.
(4) Repair methods applied in each attempt to repair the leak.
(5) “Repair delayed” and the reason for the delay if the leak is not repaired within 15 calendar days after discovery of the leak.
(6) The expected date of successful repair of the leak if the leak is not repaired within 15 days.
(7) The date of successful repair of the leak.
(1) Keep an up-to-date, readily accessible record of the continuous monitoring data required under § 63.11092(b) or § 63.11092(e). This record shall indicate the time intervals during which loadings of gasoline cargo tanks have occurred or, alternatively, shall record the operating parameter data only during such loadings. The date and time of day shall also be indicated at reasonable intervals on this record.
(A) Flare design (i.e., steam-assisted, air-assisted, or non-assisted); and
(B) All visible emissions (VE) readings, heat content determinations, flow rate measurements, and exit velocity determinations made during the compliance determination required under § 63.11092(e)(3).
(5) If an owner or operator requests approval to use a vapor processing system or monitor an operating parameter other than those specified in § 63.11092(b), the owner or operator shall submit a description of planned reporting and recordkeeping procedures.
(2) Records of actions taken during periods of malfunction to minimize emissions in accordance with § 63.11085(a), including corrective actions to restore malfunctioning process and air pollution control and monitoring equipment to its normal or usual manner of operation.
- 40 CFR 63.11087 — What Requirements Must I Meet for Gasoline Storage Tanks if My Facility Is a Bulk Gasoline Terminal, Pipeline Breakout Station, or Pipeline Pumping Station?
- 40 CFR 63.11095 — What Are My Reporting Requirements?
- 40 CFR 63.11089 — What Requirements Must I Meet for Equipment Leak Inspections if My Facility Is a Bulk Gasoline Terminal, Bulk Plant, Pipeline Breakout Station, or Pipeline Pumping Station?
- 40 CFR 63.11086 — What Requirements Must I Meet if My Facility Is a Bulk Gasoline Plant?
- 40 CFR 63.11085 — What Are My General Duties to Minimize Emissions?
- 40 CFR 63.11088 — What Requirements Must I Meet for Gasoline Loading Racks if My Facility Is a Bulk Gasoline Terminal, Pipeline Breakout Station, or Pipeline Pumping Station?
- 40 CFR 63.11125 — What Are My Recordkeeping Requirements?