49 CFR § 178.35 - General requirements for specification cylinders.
(a) Compliance. Compliance with the requirements of this subpart is required in all details.
(b) Inspections and analyses. Chemical analyses and tests required by this subchapter must be made within the United States, unless otherwise approved in writing by the Associate Administrator, in accordance with subpart I of part 107 of this chapter. Inspections and verification must be performed by -
(2) For DOT Specifications 3B, 3BN, 3E, 4B, 4BA, 4B240ET, 4AA480, 4L, 8, 8AL, 4BW, 4E, 4D (with a water capacity less than 1,100 cubic inches) and Specification 39 (with a marked service pressure 900 psig or lower), and manufactured within the United States, a competent inspector of the manufacturer.
(c) Duties of inspector. The inspector shall determine that each cylinder made is in conformance with the applicable specification. Inspections shall conform to CGA C-11 (IBR, see § 171.7 of this subchapter) except as otherwise specified in the applicable specification.
(1) Seamless cylinders. Seamless cylinders shall be inspected in accordance with Section 5 of CGA C-11. For cylinders made by the billet-piercing process, billets must be inspected and shown to be free from piping (laminations), cracks, excessive segregation and other injurious defects after parting or, when applicable, after nick and cold break.
(2) Welded cylinders. Welded cylinders shall be inspected in accordance with Section 6 of CGA C-11. Note: The recommended locations for test specimens are depicted in Figures 1 through 5 in appendix A to subpart C of part 178.
(3) Non-refillable cylinders. Non-refillable cylinders shall be inspected in accordance with Section 7 of CGA C-11
(4) Inspector's report. The inspector shall prepare a report containing, at a minimum, the applicable information listed in CGA C-11. Any additional information or markings that are required by the applicable specification must be shown on the test report. The signature of the inspector on the reports certifies that the processes of manufacture and heat treatment of cylinders were observed and found satisfactory. The inspector must furnish the completed test reports required by this subpart to the maker of the cylinder and, upon request, to the purchaser. The test report must be retained by the inspector for 15 years from the original test date of the cylinder.
(d) Defects and attachments. Cylinders must conform to the following:
(2) Metal attachments to cylinders must have rounded or chamfered corners or must be protected in such a manner as to prevent the likelihood of causing puncture or damage to other hazardous materials packages. This requirement applies to anything temporarily or permanently attached to the cylinder, such as metal skids.
(e) Safety devices. Pressure relief devices and protection for valves, safety devices, and other connections, if applied, must be as required or authorized by the appropriate specification, and as required in § 173.301 of this subchapter.
(1) Each cylinder must be marked with the following information:
(i) The DOT specification marking must appear first, followed immediately by the service pressure. For example, DOT-3A1800.
(ii) The serial number must be placed just below or immediately following the DOT specification marking.
(iii) A symbol (letters) must be placed just below, immediately before or following the serial number. Other variations in sequence of markings are authorized only when necessitated by a lack of space. The symbol and numbers must be those of the manufacturer. The symbol must be registered with the Associate Administrator; duplications are not authorized.
(iv) The inspector's official mark and date of test (such as 5-95 for May 1995) must be placed near the serial number. This information must be placed so that dates of subsequent tests can be easily added. An example of the markings prescribed in this paragraph (f)(1) is as follows:
(3) Marking exceptions. A DOT 3E cylinder is not required to be marked with an inspector's mark or a serial number.
(5) The size of each marking must be at least 0.25 inch or as space permits.
(6) Other markings are authorized provided they are made in low stress areas other than the side wall and are not of a size and depth that will create harmful stress concentrations. Such marks may not conflict with any DOT required markings.
(7) Marking exceptions. A DOT 8 or 8AL cylinder is not required to be marked with the service pressure.
(8) Tare weight or mass weight, and water capacity marking. DOT-specification 4B, 4BA, 4BW, and 4E cylinders used in liquefied compressed gas service manufactured after December 28, 2022, must be marked with the tare weight or mass weight. Additionally, the cylinder must be permanently marked with the water capacity. The owner of the cylinder must ensure it is marked with the following information, as applicable:
(i) Tare weight. The tare weight for a cylinder 25 pounds or less at the time of manufacture, with a lower tolerance of 3 percent and an upper tolerance of 1 percent; or for a cylinder exceeding 25 pounds at the time of manufacture, with a lower tolerance of 2 percent and an upper tolerance of 1 percent. The tare weight marking must be the actual weight of the fully assembled cylinder, including the valve(s) and other permanently affixed appurtenances. Removable protective cap(s) or cover(s) must not be included in the cylinder tare weight. Tare weight shall be abbreviated “TW”; or
(ii) Mass weight. The mass weight for a cylinder 25 pounds or less at the time of manufacture, with a lower tolerance of 3 percent and an upper tolerance of 1 percent; or the mass weight marking for a cylinder exceeding 25 pounds at the time of manufacture, with a lower tolerance of 2 percent and an upper tolerance of 1 percent. The mass weight marking must be the actual weight of the fully assembled cylinder, excluding valve(s) and removable protective cap(s) or cover(s). Mass weight shall be abbreviated “MW”; and
(iii) Water capacity. The water capacity for a cylinder 25 pounds water capacity or less, with a tolerance of minus 1 percent and no upper tolerance; or for a cylinder exceeding 25 pounds water capacity, with a tolerance of minus 0.5 percent and no upper tolerance. The marked water capacity of the cylinder must be the capacity of the cylinder at the time of manufacture. Water capacity shall be abbreviated “WC”.
(g) Manufacturer's reports. At or before the time of delivery to the purchaser, the cylinder manufacturer must have all completed certification documents listed in CGA C-11. The manufacturer of the cylinders must retain the reports required by this subpart for 15 years from the original test date of the cylinder.
The following state regulations pages link to this page.